10/3 cable is designed to power 220-volt outlets, such as the four-pronged outlets used to power electric dryers, air conditioners, and ranges. It is typically used in residential wiring and is designed to run on a 30-amp circuit. 10/3 cable contains 3 live wires as well as a ground wire. In contrast, the cable used to power your light switches and wall sockets is typically 10/2 wire, which has only 2 live wires and a ground wire.
Table of Contents
What Do the Numbers in 10/3 Wire Mean?
The first number in cable’s classification refers to the gauge of the wire itself. Therefore, 10/3 cable uses 10-gauge wire for each of the individual wires within the cable. Because wire gauges are retrogressive, the lower the gauge number, the thicker the wire is. So, 10-gauge wire is actually thicker than 12 and 14-gauge wire. This means 10/3 cable contains thicker wires than 12/2. This thicker gauge enables the wire to conduct higher amounts of electricity. This allows 10/3 cable to power medium-sized appliances.
- The “10” in 10/3 cable indicates the gauge of each wire in the cable.
- 10/3 cable contains 10-gauge wires.
- The “3” in 10/3 indicates the number of electrical conductor wires in the cable.
- 10/3 wire contains 3 conductor wires.
- 10/3 cable includes a 4th wire, which is the ground wire.
The “3” in 10/3 wires refers to the number of electricity-conducting wires in the cable. It does not include the ground wire. So, a 10/3 cable has red-insulated “hot” wire, a black-insulated “hot” wire, a white-insulated neutral wire, and a green-insulated or bare copper ground wire.
What is a 10/3 Wire Used For?
10/3 wire is used to wire a 220-volt outlet designed to power appliances requiring up to 30 amps of power. In the US, a 220-volt outlet is a four-pronged outlet your dryer or stove is typically plugged into. 10/3 wire can be used to wire outlets for air conditioning units, electric dryers, and small ovens or stoves.
- 10/3 wire is designed for wiring 220-volt four-pronged outlets.
- 10/3 wire is used for appliances requiring up to 30 amps.
- Dryers, air conditioners, and small stoves/ranges are commonly powered by outlets wired with 10/3
- If your appliance requires more than 30 amps of power, 10/3 will not be sufficient.
- For large appliances, wire your 220-volt socket with larger wire, such as 8/3 or 6/3 cable.
When wiring an outlet with 10/3 wire, it’s important that the wire runs to a dedicated circuit that can deliver at least 30 amps. Otherwise, you will not have sufficient electricity to run your appliance. Some home appliances, such as large stoves and ovens, require more than 30 amps. For appliances of this size, you’ll need to use a cable with a larger wire size. 8/3 and 6/3 cables are rated for appliances requiring 45 and 55 amps, respectively.
What is the Diameter of 10/3 Wire?
Most 10/3 cable has a total diameter of 0.66 inches. However, the exact diameter depends on the manufacturer of the cable. This is because the cable contains 4 10-gauge wires, insulation for the individual wires, and the cable jacket.
- The typical diameter for 10/3 cable is 0.66 inches.
- Each 10-gauge wire in 10/3 cable has a diameter of 0.1019 inches.
- Total cable diameter differs based on the manufacturer, materials used, and whether or not the ground wire is insulated.
Each individual 10-gauge copper wire within your 10/3 cable has a diameter of 0.1019 inches. Although the 3 conductor wires must be insulated, some 10/3 cable includes an insulated ground wire while other varieties simply include an uninsulated copper wire for the ground. This can alter the overall size of your 10/3 cable.
Is 10/3 Wire Heavy Enough for a Dryer?
As long as your dryer requires 30 amps or less, 10/3 cable is sufficient for the installation. This applies to most home dryers, but you should always double-check the required amperage of your appliances before running cable to the outlet.
- 10/3 cable is heavy enough for an electric dryer that requires 30 amps or less.
- Most dryers fit into this category, but verify your dryer’s amp requirements before wiring.
- Make sure your 220-volt outlet is placed on a circuit where it can safely draw 30 amps of power.
If your dryer requires 30 amps or fewer, use a 10/3 cable to wire the 220-volt outlet for the dryer. Make sure the cable is placed on a dedicated circuit where it can reliably draw 30 amps. Overloading a circuit can lead to a tripped circuit breaker or an electrical fire.
Can 10/3 Wire Be Run Underground?
10/3 cable can be safely run underground. However, you must run the cable through a conduit in many cases to protect it from breakage. Although some building codes allow for cables to be run underground if they are buried deeply enough, your safest bet is to use conduit to protect any exterior and underground cable runs.
- 10/3 cable can be run underground, provided it is properly protected.
- Check with your local building code to determine what type of conduit is required based on the depth of your cable run.
- Work with an electrician when running 10/3 cable to exterior buildings—the installation may require installing electrical subpanels.
If you are running 10/3 cable underground to an outbuilding or other outlet, it’s important to work with an experienced electrician. Local building code may require a subpanel for outbuildings. Additionally, long cable runs can result in voltage drops that fail to deliver sufficient power. A larger size wire may be required for a longer cable run.
What is a 10/3 Cable?
10/3 cable is an electrical cable commonly used in residential applications. The things you need to know before running 10/3 wire are:
- 10/3 cable contains three 10-gauge conducting wires and one 10-gauge ground wire.
- It is most-often used to wire 220-volt outlets (four-pronged outlets in the US).
- Commonly, 10/3 is used to power clothes dryers, air conditioners, and small kitchen ranges.
- 10/3 wire can serve appliances that draw up to 30 amps.
- For appliances requiring more than 30 amps, you will need cable that is heavier than 10/3.
If you are planning to run 10/3 cable as electrical wiring, make sure the cable is wired to a circuit that can provide at least 30 amps of power. When working with high-voltage electrical wire, consult a professional electrician if you are inexperienced or are planning a unique electrical installation. Building code that applies to electricity contains essential guidelines for your safety.